<?xml version="1.0" encoding="UTF-8"?>
<!-- GXML Toolbox V3.3 R20230829;  http://www.gaeb-toolbox.de/ 
 gtcConverter.dll used version 2024.07.02  -->
<GAEB xmlns="http://www.gaeb.de/GAEB_DA_XML/200407">
 <GAEBInfo>
  <Version>3.1</Version>
  <VersDate>2009-12</VersDate>
  <Date>2026-04-23</Date>
  <Time>09:58:05</Time>
  <ProgSystem>/ GXML Toolbox V3.3 R20230829</ProgSystem>
  <ProgName>iTWO_64 V24.0.796</ProgName>
 </GAEBInfo>
 <PrjInfo>
  <NamePrj>387</NamePrj>
  <LblPrj>Hans Böckler Berufskolleg</LblPrj>
  <Cur>EUR</Cur>
  <CurLbl>Euro</CurLbl>
 </PrjInfo>
 <Award>
  <DP>83</DP>
  <AwardInfo>
   <Cur>EUR</Cur>
   <CurLbl>Euro</CurLbl>
  </AwardInfo>
  <OWN>
   <Address>
    <Name1>Stadt Münster</Name1>
    <Street>Albersloher Weg 33</Street>
    <PCode>48155</PCode>
    <City>Münster</City>
    <Country>Deutschland</Country>
    <Contact>Benedict Schäfer</Contact>
    <Phone>2529</Phone>
    <Email>schaeferb@stadt-muenster.de</Email>
   </Address>
  </OWN>
  <AddText>
   <OutlineAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span>Baubeschreibung</span>
    </p>
   </OutlineAddText>
   <DetailAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">                    </span>
     <span style="font-family:Arial;font-weight:bold;font-size:12pt;Color:rgb(0,0,0);">Baubeschreibung</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Baubeschreibung</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lieferung und Montage von Chemieraumausstattung als Komplettpaket</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Verbindliche Ausführungsfristen</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lieferung der Werkplanung (Installationsplan und Kabelzugliste, einschl. aller Medienanschlusspunkte)</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">spätestens KW 35 2026 24.08. - 28.08.26</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lieferung und Montage Deckenunterkonstruktion</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">spätestens KW 11 2027 22.03. - 25.03.27</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lieferung und Montage deckengebundenes Mediensystem und Chemieraumeinrichtung</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">spätestens KW 14-15 05.04. - 16.04.27</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Baustelle</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gebäudebezeichnung: Hans-Böckler Berufskolleg</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gebäudenutzung: Berufsschule</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ort: Hoffschultestraße 25, 48155 Münster</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bauvorhaben: Fachraumsanierung Chemie</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lage: Raum 101 und 102 (zusammgelegt), 1.Obergeschoss</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">LV-Gegenstand: Fachraumausstattung einschl. Nebenleistungen</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Schulgebäude</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Das Schulgebäude wurde 1962 errichtet und fungiert als Berufskolleg (Schule der Sekundarstufe II) mit den Schwerpunkten Chemie-, Elektro-, Informations- und Metalltechnik. Das 5-geschossige Schulgebäude unterteilt sich in ein Hauptgebäude, zwei Anbauten von 1980 und 2003 und Dachaufstockungen von 1990 und 2001. Das Gebäude ist nur im südlichen Gebäudeabschnitt unterkellert, der restliche Gebäudeteil hat einen Kriechkeller.</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Bauliche Gegebenheiten</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zufahrt: Das Schulgebäude ist über die Hoffschultestraße zu befahren. Das Material ist über den Hintereingang über das Treppenhaus 2 und den vorhandenen Aufzug in das 1. Obergeschoss zu transportieren. Die schuleigenen WC-Anlagen können mitbenutzt werden.</span>
    </p>
    <p style="margin-left:70pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:70pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Maßnahme</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">In diesem LV werden Komplettleistungen für eine Chemieraumausstattung abgefragt. Für Arbeiten die außerhalb der Ferien durchgeführt werden ist auf Schüler und Lehrer besonders Rücksicht zu nehmen. Lärmverursachende Arbeiten sind mit der Bauleitung bzw. der Schulleitung abzustimmen. Arbeitstäglich ist anfallender Schutt zu beseitigen und Verschmutzungen durch den AN im Gebäude und auf dem Schulhof umgehend zu beseitigen. Die Leistungen verstehen sich als fix und fertige Arbeiten einschließlich Nebenleistungen. Die Baustelleneinrichtung erfolgt vom AN in Abstimmung mit der städtischen Bauleitung.</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Auf Verlangen hat der Bieter kostenneutrale Muster zur</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verfügung zu stellen. Diese Muster sind Teil des Angebotes und</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">werden nicht gesondert vergütet. Bemusterung und</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbgestaltung sind an anderer Stelle ausführlich beschrieben.</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Bieter hat im Auftragsfall alle Maße am Bau zu prüfen und</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">bei Abweichungen in Eigeninitiative dem Bauherren</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Änderungsvorschläge zu unterbreiten. Die technische</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Projektierung bzw. Erstellung der Werkstattzeichungen und der</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wandansichtspläne haben aufgrund der technischen</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Komplexität des Projekts und der Abstimmung mit den anderen</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewerken in geeigneter 2D - Darstellung zu erfolgen. Die Kosten</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für die Erstellung dieser Pläne, sowie die digitale Bereitstellung der Pläne und Revisionsunterlagen werden nicht gesondert vergütet.</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sämtliche Labormöbel sind innen und außen sauber aus- bzw.</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">abgewischt zu übergeben. Tischplatten sowie Ablagen sind vor</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der Übergabe ebenfalls zu reinigen.</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Liefer- und Leistungsgrenzen</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">1 Gewerk Sanitär</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Trinkwasserschutz nach DIN 1988, Teil 4, w ird bauseitig</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vorgesehen. (Die Trinkwasserversorgung ist abhängig von der</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gefahrenklasse gem . EN 1717 und wird separat d.h. bauseitig</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">/ eingebaut)</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefergrenze</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Verrohrung innerhalb der Systeme</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Versorgungs - Leitungen - Auftragsnehmer</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Entsorgungs - Leitungen - Auftragsnehmer</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Tischanbindung</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Material - Versorgungs -Anschluss - Auftragnehmer</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Material - Entsorgungs -Anschluss - Auftragnehmer</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Anschlussarbeiten Ver-/ Entsorgung - Auftragnehmer</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bauseitge Vorleistungen</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Heranführen der Hausinstallation bis in den Bereich der</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Installationsräume der System sowie das Setzen der</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Absperrventile</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <br/>
     <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">2 Gewerk Elektro</span>
     <br/>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefergrenze</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Verdrahtung der elektrischen Einbaugeräte endend auf Reihenklemmen in</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">integrierten Kleinverteiler - Auftragnehmer</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Absicherung der Stromkreise mit Leitungsschutz -</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">schalter - Auftragnehmer</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Tischanbindung (Verbindung mt dem Hausnetz) incl .</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Endprüfung nach VDE 0100 Teil 600 - Auftragnehmer -</span>
     <br/>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Es sind alle einschlägigen Vorschriften wie</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">EU - Normen, DIN, DVGW, GS - Zeichen, VDE -, VGB - und</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">VDI - Richtlinien und die sonst behördlichen Vorschriften und</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bauauflagen zu berücksichtigen , die für die Fertigung von</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Laboreinrichtungen gültig sind . Im Einzelnen sind mit dem</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Angebot einzureichen :</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">GS - Zeichen für :</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Lehrerexperimentiertisch</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Lehrertisch - Schutzscheibe</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Schülerexperimentiertische</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Deckenversorgungssystem</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(fest und höhenvestellbar)</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Schränke</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Säuren und Laugenschränke</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Chemikalienschränke</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Sicherheitsschränke für brennbare Flüssigkeiten</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- alle enthaltenen Abzüge</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lufttechnisches Prüfprotokoll für alle enthaltenen Abzüge</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bei Nichtvorlage der GS - Zeichen und Prüfprotokolle werden</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">diese als nicht vorhanden gewertet.</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verzeichnis .</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Richtlinien / Sicherheitsanforderungen</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">BGI / GUV I 850-0 / GUV SI 8070 TRGS 526 / TRBA 100</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">desweiteren</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">BG - 1 7850-0, BGS 121 (bisherig ZH 1/140), TRGI 2009 -D VGW</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">A rbeitsblatt G 621 (Technische Regeln für Gasinstallation)</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">TRF 2012 (Technische Regeln Flüssiggas)</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">GUV - SI 8070 , GUV - V S 1  etc .</span>
     <br/>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN -/ EN - Normen :</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1. Laborplanung und allgemeine Laboreinrichtung</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN 1946 Teil 7 Raumlufttechnische Anlagen in Laboratorien</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN 12 000 Graphische Symbole und Sicherheitszeichen</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN EN 13 792 Farbkennzeichnung der Armaturen</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN EN 14 056 Laboreinrichtung - Empfehlung , Anordnung</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und Montage</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2. Laborarmaturen</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN 12898 Laborarmaturen: Schlauchtüllen</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN 12918 Laboreinrichtungen: Laborarmaturen , Teil 1</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Entnahmestellen für Wasser</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN 12918 Teil 2 Laboreinrichtungen, Teil 2 Entnahmestellen</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für Brenngase</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN 3537 Teil 3 Gasabsperrarmaturen bis PN 4</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN EN 13 792 Farbige Kennzeichnung von Laborarmaturen</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN EN 15 154-1 Sicherheitsnotduschen - Teil 1: K örperduschen</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Wasseranschluss in Laboratorien .</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN EN 15 154-2 Sicherheitsnotduschen - Teil 2: Augenduschen</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Wasseranschluss</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">3. Labortische und Schränke</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN 12 912 Laboreinrichtungen: Keramische Fliesen für</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Labortische</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN 12 915 Laboreinrichtungen: Einbauecken aus</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">keramischen Werkstoffen</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN 12 916 Laboreinrichtungen: Großformatige</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Labortischplatte</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN EN 13 150 Arbeitstische für Laboratorien - Maße, Sicherheitsanforderungen</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und Prüfverfahren</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN EN 14 727 Labormöbel Schränke und Regale für Laboratorien</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Anforderungen und Prüfverfahren</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">4. Sicherheitsschränke</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN EN 14 470-1 Feuerwiderstandsfähige Lagerschränke</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Teil 1: Sicherheitsschränke für brennbare Flüssigkeiten</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN EN 14 470-2 Feuerwiderstandsfähige Lagerschränke</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Teil 2: Sicherheitsschränke für Druckflaschen</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">5. Laborabzüge</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN 25 466 Radionuklidaabzübe - Regeln für die Auslegung</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und Prüfung</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN EN</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">6. Laborabzüge</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN EN 14 175-1 Abzüge - Teil 1: Begriffe - Bauarten, Bauteile</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Arten von Abzügen etc.</span>
     <br/>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN EN 1 4 175-2 Abzüge - Teil 2: A nforderungen an</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sicherheit</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und Leistungsvermögen , Baumaße itc .</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN EN 175-3 Abzüge - Teil 3 : Baumusterprüfverfahren</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN 12 924-3 Abzüge - Durchreicheabzüge , Hauptmaße</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anforderungen und Prüfungen</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">7 . Weitere DIN / EN - Normen</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN 57 789 / VDE 0789 Teil 100 , Unterrichtsräume</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und Laboratorien : Regeln - und Laborgeräte</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">EN 61010 Teil 1 Sicherheitsbestimmungen für elektrische</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mess - , Steuer - , Regel - VDE 0411 - Teil 1 und Laborgeräte-</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN 18 355 Tischlerarbeiten</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN 18 357 Beschlagarbeiten</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN 18 360 Metallbauarbeiten , Schlosserarbeiten</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN 18 381 Gas - , Wasser - , und Abwasser</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">installationsarbeiten</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN 18 382 Elektrische Kabel - und Leitungsanlagen in</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gebäuden</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN 18 421 Dämmarbeiten an technischen Anlagen</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN EN ISO 9001 Qualittätsmanagement</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">BS - OHSAS 18001 Arbeitssicherheitsmanagement</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN VDE 0100-600 Inbetriebnahme Elektrische Anlagen</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN VDE 0105-100 Betreiben Elektrischer Anlagen</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Allgemeine Festlegungen</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Desweiteren sind alle einschlägigen Vorschriften wie</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">EU - Normen, DIN, DVGW, GS - Zeichen, VDE - ,VGB - und</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">VDI - Richtlinien und die sonst behördlichen Vorschriften und</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bauauflagen zu berücksichtigen , die für die Fertigung von</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Laboreinrichtungen gültig sind . Im Einzelnen sind mit dem</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">A ngebot einzureichen:</span>
    </p>
    <p style="margin-left:56pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">GS - Zeichen für:</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Lehrerexperimentiertisch</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Lehrertisch - Schutzscheibe</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Schülerexperimentiertische</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Deckenversorgungssystem</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(fest und höhenvestellbar)</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Schränke</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Säuren und Laugenschränke</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Chemikalienschränke</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Sicherheitsschränke für brennbare Flüssigkeiten</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- alle enthaltenen Abzüge</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lufttechnisches Prüfprotokoll für alle enthaltenen Abzüge</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">( gem . DIN 14175 T 3)</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bei Nichtvorlage der GS - Zeichen und Prüfprotokolle werden diese als nicht vorhanden gewertet.</span>
    </p>
    <p style="margin-left:70pt;margin-right:127pt;text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;"/>
   </DetailAddText>
  </AddText>
  <BoQ ID="AAAAAAAAICFNAAAA">
   <BoQInfo>
    <Name>44</Name>
    <LblBoQ>Fachraumausstattung Chemie</LblBoQ>
    <Date>2026-04-23</Date>
    <OutlCompl>AllTxt</OutlCompl>
    <BoQBkdn>
     <Type>BoQLevel</Type>
     <LblBoQBkdn/>
     <Length>2</Length>
     <Num>Yes</Num>
    </BoQBkdn>
    <BoQBkdn>
     <Type>BoQLevel</Type>
     <LblBoQBkdn/>
     <Length>2</Length>
     <Num>Yes</Num>
    </BoQBkdn>
    <BoQBkdn>
     <Type>Item</Type>
     <Length>4</Length>
     <Num>Yes</Num>
    </BoQBkdn>
    <BoQBkdn>
     <Type>Index</Type>
     <Length>1</Length>
     <Num>No</Num>
     <Alignment>left</Alignment>
    </BoQBkdn>
   </BoQInfo>
   <BoQBody>
    <Remark ID="AAAAAAAAICFNEKHA">
     <Description>
      <CompleteText>
       <DetailTxt>
        <Text>
         <p style="margin-left:-70pt;text-align:center;margin-top:0pt;margin-bottom:0pt;">
          <span style="font-family:Arial;font-weight:bold;font-size:16pt;Color:rgb(0,0,0);">LEISTUNGSBESCHREIBUNG</span>
         </p>
        </Text>
       </DetailTxt>
       <OutlineText>
        <OutlTxt>
         <TextOutlTxt>
          <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
           <span>Leistungsbeschreibung</span>
          </p>
         </TextOutlTxt>
        </OutlTxt>
       </OutlineText>
      </CompleteText>
     </Description>
    </Remark>
    <BoQCtgy ID="AAAAAAAAICHNAAAA" RNoPart="1">
     <LblTx>
      <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
       <span>Fachraumausstattung Chemie</span>
      </p>
     </LblTx>
     <BoQBody>
      <BoQCtgy ID="AAAAAAAAICHNAOOA" RNoPart="1">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>Medienversorgungssystem und Abzug</span>
        </p>
       </LblTx>
       <BoQBody>
        <Itemlist>
         <Item ID="AAAAAAAAICHNEAAA" RNoPart="10">
          <Qty>1.000</Qty>
          <QU>Stk</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschlusseinheit für deckengebundenes Medienversorgungssystem zur Elektro-, Gas- und Sanitärversorgung</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rahmen aus Stahlblech pulverbeschichtet RAL 7040</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fenstergrau;</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Blende oben für die Einführung des Deckenkanalsystems,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hängeschrank für Elektro-Unterverteilung,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abtropfgestell an Flügeltüre über Becken mit</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">integrierter Abtropfwanne und</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ablaufröhrchen;</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">6 Panels mit bestückbaren Medienfeldern,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Spritzschutzblende H = 327 mm;</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">B/H/T = 1200/2700/350 mm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hängeschränke 600+600mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausführung Zelle Abtropfgitter rechts</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Breite 1200 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe Korpus weiß, Front weiß</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Frontausführung Tür links + rechts, verschließbar</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Höhe 2700 mm, Tiefe 274 mm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Armatur Mischbatterie 1 Auslass</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Tülle</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Handaugendusche, 1 Duschkopf,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">arretierbares Klappventil, Zulassung</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">nach DIN/DVGW, min. Arbeitsdruck 1 bar, max.</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Arbeitsdruck 10 bar, Temperaturbereich 5-80 °C,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Druckschlauch L = 1500 mm mit Gegengewicht</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Hydraulisch gesteuerter Durchlauferhitzer</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit 6,5 kW, Leistung / 400V</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gas-Sicherheits-Technik</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Doppelmagnetventil VCL mit Geschlossenheitskontrolle</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Doppelmagnetventil VAL mit Geschlossenheitskontrolle</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Laborsteuerung LCU für Ventile</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Druckminderer für Gasflasche 50mbar</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hauptschalter Elektro</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Drucktaster rot (Öffner), Lichtgrau</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Schlüsseltaster inkl. 2 Schlüssel, Lichtgrau</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Not-Aus (1-polig) beleuchtet, Gelb/Rot</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Leuchtmelder grün 230V, Lichtgrau</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Taster Steuerung Gas (Lehrer/Schüler)</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2x EIN/AUS Taster mit LED-Kontrollleuchte 18-30V,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lichtgrau</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Drucktaster mit LED-Kontrollleuchte rot 18-30V,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lichtgrau</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Displayanzeige 1,3 Zoll OLED,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für Geschlossenstellungs- und</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leckageprüfung inkl. Timer und</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fehleranzeige</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">11x Taster Auf/Ab für Medienentnahmestellen</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(Entnahmestellen einzeln abschwenkbar)</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">3x Wipptaster, Lichtgrau</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Beleuchtung Links/Mitte/Rechts</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2x EIN / AUS Taster mit LED-Kontrollleuchte 230V,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lichtgrau, Elektro Lehrer/Elektro Schüler</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Steckdose 230V</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2x Blindplatte 64mm, Lichtgrau</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Verteiler mit kompletter Unterverteilung für die</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fachraumeinrichtung (inkl. Überspannungsschutz)</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Spülenvorbau für Anschlusszelle</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">B/H/T = 1200/900/675 mm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Tischplatte B/T: ca.1200/675mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">30 mm Steinzeug-Verbund Weiß, 7 mm PUR Wulstrand,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Becken Steinzeug 445x445mm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Unterbau Spüle mit Flügeltür links,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">B/H/T = 600/870/550mm, verschließbar</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Unterbau Gasflasche mit Flügeltür rechts,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">B/H/T = 600/870/550mm, verschließbar</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Propangasflasche, Stahl Olivgrau, Ventilschutzkappe</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stahl Rot, 5kg: Ø = 229 mm, H = 485 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mit Füllung</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Datenschrank 19 Zoll</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einteiliges geschweißtes Wandgehäuse IP20, 6HE, grau</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">RAL 7035</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Vollglastüre aus 4 mm starkem stoßfesten gehärteten</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Glas, abschließbar, einfach abbaubar</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">B/H/T: 600/370/395 mm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Netzwerkleitung mit 21 mtr. Überlänge im Baukörper</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zu verlegen</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Durchgangsprüfung Datenleitung</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Netzwertester</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Funktionsmessung</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Ping-Test</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Längenmessung</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Lokalisierung von Störungen</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Anschlusszelle</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAICHNFAAA" RNoPart="20">
          <Qty>1.000</Qty>
          <QU>Stk</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Medienversorgungssystem als Komplettsystem, deckengebunden</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Deckensystem bestehend aus Kanälen, Abhängungen und</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Entnahmestellen (keine Leitungsverlegung in oder an der</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">abgehängten Decke, Leitungszuführung auf einer Ebene</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit dem Kanalsystem, das Kanalsystem muss geschlossen</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">sein bis zu einer Höhe von 2250 mm)</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gesamtlänge Kanalsystem ca. 35 m, inkl. aller</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">benötigten Verbindungselemente</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Elektromotorisch abschwenkbare Entnahmestelle Lehrer</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Entnahmestelle abgeschwenkt</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-2x Gasarmatur für Flüssiggas</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-4x Steckdose 230V</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-1x Not-Aus (1-polig), Gelb/Rot</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-1x HDMI-Buchse</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-1x Datendoppeldose 2x RJ45 CAT 6 A, Lichtgrau</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-1x USB-Doppellade-Buchse Typ C</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-1x Absperrventil zur Ausfallsicherung</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-1x Extender für HDMI zur Verbindung zwischen Quelle</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und Tafelanlage/Beamer/Board Display Übertragung bis</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">30m über Netzwerkkabel RJ45; HDMI-CAT6-HDMI; inklusiv</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zwei HDMI-Kabel (2m+5m)</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Entnahmehöhe Medien-Versorgungsstelle auf Augen- u. Greifhöhe der Lehrer zwischen 1,35 m und 1,70 m ü. OKFF in</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">abgesenktem Zustand</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">10x Elektromotorisch abschwenkbare Entnahmestelle</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schüler</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Entnahmestelle abgeschwenkt</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-2x Gasarmatur für Flüssiggas</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-5x Steckdose 230V</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-1x Datendoppeldose 2x RJ45 CAT 6 A, Lichtgrau</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-2x USB-Doppellade-Buchse Typ C</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-1x Absperrventil zur Ausfallsicherung</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Entnahmehöhe Medien-Versorgungsstelle auf Augen- u. Greifhöhe der Schüler zwischen 1,35 m und 1,70 m ü. OKFF in</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">abgesenktem Zustand</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">16x LED - Doppelleuchte</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Digital Dimmbar über DALI-Steuerung,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gleichmäßige und blendfreie Ausleuchtung der</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Arbeitsplätze durch 30 % direkten und 70 %</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">indirekten Lichtanteil, Abstrahlung nach oben und</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">unten 4000 K, Lichtstrom 6550 Lumen, Farbwiedergabe Index CRI 94, nach DIN EN 12464, Gehäuse aus Aluminium pulverbeschichtet RAL 7035 Lichtgrau, Anschlusswert 220-240 V, Leistung 68 W, 600/140/410 mm (B/H/T)</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Vormontagematerial (separater Termin zur Vormontage)</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Das Vormontagematerial enthält die Basiskonstruktion</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zur Montage der Medienversorgung an die Raumdecke;</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bestehend aus: C-Profilschienen, Gewindestangen M10,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Versteifungs-profilen aus stranggepresstem Aluminium</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">pulverbeschichtet (für UZG/Rippendecke), alle</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">notwendigen Kleinteile</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Deckenversorgungssystem</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAICHNGAAA" RNoPart="30">
          <Qty>1.000</Qty>
          <QU>Stk</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Stationärer Demonstrationsabzug vollverglast,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschluss an Deckensysteme oder Experimentiertisch,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Arbeitshöhe 900 mm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Von allen Seiten uneingeschränkt einsehbar durch</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vollverglaste Versuchsplattform und konvexe vordere</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sichtscheibe;</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Glaselemente aus Einscheiben-Sicherheitsglas (ESG);</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schülerseite: konvexe Scheibe,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lehrerseite: zweiteiliger</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Frontschieber mit Fallsicherung aus</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Aluminium-Strangpressprofil RAL 7040 Fenstergrau,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vertikal verschiebbar mit Endstopper und 2 horizontal</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">gegenläufigen Schiebefenstern,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">darunter 2 kleinere horizontal gegenläufige</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Frontschiebefenster, Schiebefenster mit</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kunststoffgriffen; </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Energiesparende und blendfreie</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Innenbeleuchtung Downlight 2x 26 W;</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Arbeitsplatte Steinzeug mit umlaufendem PP-Wulstrand;</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zugang zum Installationsraum</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">unter dem Abzugsinnenraum durch beidseitige</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Querrolladen; Abluftstutzen Ø = 125 mm; 2x</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Steckdose 230 V, 16 A mit Klappdeckel im</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abzugsinnenraum; Funktionsanzeige mit Tastenfunktion</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">in Augenhöhe am Außenrahmen; Mikroelektronische</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Überwachung der Abzugsfunktion nach DIN 12924 Teil 1;</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mindestvolumenstrom 300 m3/h nach EN 14175 Teil 3</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">B/H/T = 1060/1975/835 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mit Gasarmatur</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mit Wasserarmatur</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mit Hebeanlage zur Wasserrückführung</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Steigkanal für stationären Demonstrationsabzug</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">bis Abzugsoberkante</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stahlblechkonstruktion pulverbeschichtet RAL 7035</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lichtgrau Profil zur seitlichen Montage</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Elektrobestückung (von oben nach unten)</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Not-Aus</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Datendoppeldose</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Steckdose 230V lichtgrau</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Webcam</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">HD-Videoqualität 1080p mit 30 Bildern pro</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sekunde</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Erweitertes Blickfeld - 90 Grad</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mit skalierbarer Videokodierung</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schwenk-, Kipp- und Zoomfunktion,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">4-fach-Zoom bei 1080p</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mit Abdeckblende für Privatsphäre und Sicherheit</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Plug&#x26;Play-USB-Verbindung</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Saugnapf und GorillaPod Arm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Flexibler Saugnapf für Montage, leicht montierbar</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Extender with Power over Ethernet</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für Anschluss Kamera an Abzug</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Schaltnetzteil 230 V für Webcam</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">100-240 V, 50/60 Hz, 0,25 A</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabellänge ca. 1,5 m</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2x Patchkabel Kat6 / RJ45, 1,5 m,</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Stationärer Abzug</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
        </Itemlist>
       </BoQBody>
      </BoQCtgy>
      <BoQCtgy ID="AAAAAAAAICHNBOCI" RNoPart="2">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>Arbeitsplätze</span>
        </p>
       </LblTx>
       <BoQBody>
        <Itemlist>
         <Item ID="AAAAAAAAICHNKAAA" RNoPart="10">
          <Qty>1.000</Qty>
          <QU>Stk</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lehrerarbeitsplatz, bestehend aus den folgenden Bestandteilen:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x O-Fuß-Rechtecktisch</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Seitliche Gestellrahmen aus Stahlrechteckrohr 60/25/2</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mm pulverbeschichtet,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Je 2 Längszargen oben und 1 Längszarge unten aus</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stahlrechteckrohr 60/25/2 mm pulverbeschichtet,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Doppellenkrollen, Durchmesser 100 mm, Belastbarkeit je</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rolle 100 kg</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rollengehäuse und Radfelge aus Polyamid,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rollenbereifung aus spurenfreiem Polyurethan,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schwenklager mit kombiniertem Gleitkugellager</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Tischbreite 1200 mm, Tischhöhe 900 mm, Tischtiefe 750 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Arbeitsplatte 30 mm Steinzeug-Verbund Weiß mit großflächigem Keramikbelag 8mm dick, 7 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">PUR Wulstrand</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vollständig absenkbare, auf ganzer Tischlänge verschiebbare Schutzscheibe 5mm VSG</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Unterschrank</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1 Flügeltür geschlossen,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fachböden im Raster verstellbar,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Auf unterem Boden aufgesetzt,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schrankhöhe 530 mm, Breite 450 mm, Tiefe 550 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">verschließbar</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Schubkasten-Unterschrank</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">3 Schubkästen, Höhe 2x150, 1x200 mm,</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">als Vollauszug mit Teleskopführung und Einzugsautomatik.</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mit Wechselauszugssperre,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Auf unterem Boden aufgesetzt,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schrankhöhe 530 mm, Breite 450 mm, Tiefe 550 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">verschließbar</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x O-Fuß-Rechtecktisch</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Seitliche Gestellrahmen aus Stahlrechteckrohr</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">60/25/2 mm pulverbeschichtet,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Je 2 Längszargen oben und 1 Längszarge unten aus</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stahlrechteckrohr 60/25/2 mm pulverbeschichtet,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Doppellenkrollen, Durchmesser 100 mm, Belastbarkeit je</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rolle 100 kg</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rollengehäuse und Radfelge aus Polyamid,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rollenbereifung aus spurenfreiem Polyurethan,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schwenklager mit kombiniertem Gleitkugellager</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Tischbreite 900 mm, Tischhöhe 900 mm, Tischtiefe 750 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Arbeitsplatte 30 mm HPL Weißgrau, 8 mm PUR Kante</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mit Unterboden</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x 1-Säulen Rechtecktisch, stufenlos höhenverstellbar</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(845-1260 mm) mit Gasdruckfeder,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Tischplatte klappbar</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Tischplatte 25 mm HPL Weißgrau mit PP-Kante</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fußausführung 4 Lenkrollen feststellbar</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Drehstuhl</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sitzschale aus luftgepolstertem Kunststoff,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stufenlos höhenverstellbar mit Gasdruckfeder mit integriertem Auslösehebel, Ergonomisch geformte Sitzschale aus doppelwandigem luftgepolstertem Polypropylen (100 %</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">recyclebar) mit robuster Oberflächenstruktur, Griffloch im unteren Lehnenbereich, 2 individuell beschriftbare Rückenfelder, Zweite Sitzposition &#x22;Rittlings&#x22; durch taillierten</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sitz-Lehnenübergang, Gestell aus Stahlrundrohr 22/2,5 mm pulverbeschichtet, 5-strahliges Fußkreuz aus Aluminium pulverbeschichtet Fußausführung Lenkrollen</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sitzhöhe 515 - 715 mm inkl. Fußring</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Lehrerarbeitsplatz</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAICHNLAAA" RNoPart="20">
          <Qty>1.000</Qty>
          <QU>Stk</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schülerarbeitsplätze, bestehend aus den folgenden Bestandteilen:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">14x Übungstisch, 4-Fuß Rechtecktisch</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zargen aus Stahlrechteckrohr 50/20/2 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">pulverbeschichtet,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Beine aus Stahlrundrohr 40/2 mm pulverbeschichtet,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fußausführung H = 60 mm aus Kunststoff RAL 7016</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anthrazit,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wechselbare Füße durch modulares Fußkonzept</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Tischbreite 1200 mm, Tischhöhe 800 mm, Tischtiefe 600 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Arbeitsplatte 30 mm Steinzeug-Verbund Weiß mit großflächigem Keramikbelag 8mm dick, PUR-Kante</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fußausführung TPE Gleiter</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mit Stahlkorbablagen zur Stuhlaufhängung</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(Keine Aufhängung an Tischplatte gewünscht)</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">28x Drehstuhl</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sitzschale aus luftgepolstertem Kunststoff,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stufenlos höhenverstellbar mit Gasdruckfeder mit integriertem Auslösehebel, Ergonomisch geformte Sitzschale aus doppelwandigem luftgepolstertem Polypropylen (100 %</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">recyclebar) mit robuster Oberflächenstruktur, Griffloch im unteren Lehnenbereich, 2 individuell beschriftbare Rückenfelder, Zweite Sitzposition &#x22;Rittlings&#x22; durch taillierten</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sitz-Lehnenübergang,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gestell aus Stahlrundrohr 22/2,5 mm pulverbeschichtet,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">5-strahliges Fußkreuz aus Aluminium pulverbeschichtet</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fußausführung Kunststoffgleiter</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sitzhöhe 400 - 530 mm</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Schülerarbeitsplätze</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
        </Itemlist>
       </BoQBody>
      </BoQCtgy>
      <BoQCtgy ID="AAAAAAAAICHNCNAI" RNoPart="3">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>Laborspülenblock</span>
        </p>
       </LblTx>
       <BoQBody>
        <Itemlist>
         <Item ID="AAAAAAAAICHNPAAA" RNoPart="10">
          <Qty>1.000</Qty>
          <QU>Stk</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Laborspülenblock, bestehend aus den folgenden Bestandteilen:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Modular aufgebautes Spülenmodul</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Systemhöhe 900 mm, Breite 900 mm, Tischtiefe 750 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Arbeitsplatte 30 mm Steinzeug-Verbund Weiß, 7 mm PUR</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wulstrand, rechts gestoßen</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einbaubecken Steinzeug weiß, 445/250/445 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Standsäule Kaltwasser mit Tülle und Rohrunterbrecher</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Spülen-Unterbau</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2 Flügeltüren geschlossen,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Sichtrückwand inkl. Sockel,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sockelhöhe 110 mm anthrazit,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Höhe ohne Arbeitsplatte/Abdeckung 870 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Breite 900 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">verschliessbar</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Modular aufgebautes Spülenmodul</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Systemhöhe 900 mm, Breite 1200 mm, Tischtiefe 750 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Arbeitsplatte 30 mm Steinzeug-Verbund Weiß, 7 mm PUR</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wulstrand, links und rechts gestoßen</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einbaubecken Steinzeug weiß, 445/250/445 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Abtropffläche</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Standsäule Kaltwasser mit Tülle und Rohrunterbrecher</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Standsäule VE-Wasser mit Tülle</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Absperrung für Kaltwasser</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Anschlussset für Purifikator + Armatur</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Anschluss 230V für Purifikator</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Spülen-Unterbau</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2 Flügeltüren geschlossen,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Sichtrückwand inkl. Sockel,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sockelhöhe 110 mm anthrazit,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Höhe ohne Arbeitsplatte/Abdeckung 870 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Breite 900 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">verschliessbar</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Aqua-Purifikator zur Wasseraufbereitung mit</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leitfähigkeitsmessgerät, Aufnahmeschrank für bis zu 2</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wasservollentsalzungspatronen; Sockelblende Anthrazit;</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschluss: 230 V, 16 A; Fließdruck: 250-1000 kPa;</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">B/H/T = 300/835/600 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Miele PG8595 oder gleichwertig</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Wasservollentsalzungspatrone</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">aus Edelstahl, für Purifikator, Druckfest bis 10</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">bar, Kapazität 2800 L bei 10° dH GSG, Ø = 240 mm, H =</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">600 mm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Arbeitsplatte 30 mm Steinzeug-Verbund Weiß, 7 mm PUR</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wulstrand, links und rechts gestoßen, B/T 900/750 mm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Schubkasten-Unterschrank</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">4 Schubkästen, Höhe 1x150, 3x200 mm,</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">als Vollauszug mit Teleskopführung und Einzugsautomatik.</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mit Wechselauszugssperre,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Sichtrückwand inkl. Sockel,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schrankhöhe 870 mm, Breite 900 mm, Tiefe 550 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">verschließbar</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Modular aufgebautes Spülenmodul</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Systemhöhe 900 mm, Breite 1200 mm, Tischtiefe 750 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Arbeitsplatte 30 mm Steinzeug-Verbund Weiß, 7 mm PUR</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wulstrand, links gestoßen</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einbaubecken Steinzeug weiß, 445/250/445 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Abtropffläche</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Standsäule Kaltwasser mit Tülle und Rohrunterbrecher</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Anschluss 230V für Kühlschrank</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Spülen-Unterbau</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1 Flügeltür geschlossen,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Sichtrückwand inkl. Sockel,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sockelhöhe 110 mm anthrazit,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Höhe ohne Arbeitsplatte/Abdeckung 870 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Breite 600 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">verschliessbar</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Unterbaukühlschrank mit Gefrierfach</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nutzinhalt Kühlfach: 116,3 l</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nutzinhalt Gefrierfach: 16 l</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Energieeffizienzklasse: E</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">B/H/T: 600/820/570 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liebherr UK 1524-26 oder gleichwertig</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">3x Abtropfgestell Stahldraht</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Medienabnahmestellen sind im Möbel vorinstalliert,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">d.h. die Armaturen sind eingebaut und mit den</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschlussleitungen bis zum Übergabepunkt geführt</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Laborspülenblock</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
        </Itemlist>
       </BoQBody>
      </BoQCtgy>
      <BoQCtgy ID="AAAAAAAAICHNOGJA" RNoPart="4">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>Labormobiliar</span>
        </p>
       </LblTx>
       <BoQBody>
        <Itemlist>
         <Item ID="AAAAAAAAICHOAHAI" RNoPart="10">
          <Qty>1.000</Qty>
          <QU>Stk</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schrankwand, bestehend aus den folgenden Bestandteilen:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Hochschrank für max. 5 Ordnerhöhen</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1 Flügeltür vollverglast,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fachböden im Raster verstellbar,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sockelhöhe 110 mm anthrazit</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Höhe 2090 mm, Breite 600 mm, Tiefe 550 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Innenausstattung Fachboden fest 4x</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">verschließbar</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2x Hochschrank für max. 5 Ordnerhöhen</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2 Flügeltüren vollverglast,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fachböden im Raster verstellbar,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sockelhöhe 110 mm anthrazit</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Höhe 2090 mm, Breite 1200 mm, Tiefe 550 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Innenausstattung Fachboden fest 3x unten</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Oben mit 2 Mittelwänden,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Innenausstattung 3x8 Auszugsblenden</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einschl. Griffen</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">verschließbar</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2x Garagenschrank für max. 3 Lernschränke 3x1</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2 Flügeltüren vollverglast mit Schleppsockel aus</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stahlblech,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Oben mit 2 Mittelwänden,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Innenmaß oberes Fach B/H/T = 3x 322/769/452 mm,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fester Zwischenboden,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Innenmaß unteres Fach B/H/T = 1161/1280/563 mm,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sockelhöhe 110 mm anthrazit</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Höhe 2090 mm, Breite 1200 mm, Tiefe 600 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Innenausstattung 3x8 Auszugsblenden</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einschl. Griffen</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">verschließbar</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Aufsatzschrank</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1 Flügeltür voll,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Einhängeschiene für Leiter</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fachböden im Raster verstellbar,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sockelhöhe 110 mm anthrazit</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Höhe 760 mm, Breite 600 mm, Tiefe 550 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Innenausstattung Fachboden fest 1x</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einschl. Griffen</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">verschließbar</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">4x Aufsatzschrank</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2 Flügeltüren voll,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Einhängeschiene für Leiter</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fachböden im Raster verstellbar,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sockelhöhe 110 mm anthrazit</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Höhe 760 mm, Breite 1200 mm, Tiefe 550 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Innenausstattung Fachboden fest 1x</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einschl. Griffen</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">verschließbar</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leiterschiene</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Als Metallschiene zwischen Schrank und Aufsatzschrank</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">fest verankert, Dicke min. 2 mm; mit Aussparungen zum</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einhängen einer Anlegeleiter; Schranktüren bei</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">eingehängter Leiter zu öffnen.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">6x Lernschrank</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Korpus von mehreren Seiten zugänglich mit Prallschutz,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fachböden höhenverstellbar, Fächer passend für</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lernboxen, Lernablagen und Lernordner</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">364/1130/475 mm (B/H/T)</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Korpus- und Fachbodenfarbe Weiß</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Orgablende links/rechts</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">4 Lenkrollen feststellbar</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Spalte 1 Auszugsblech</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">12x Lernbox a</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Polypropylen, stapelbar,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">BxHxT 312x150x427 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">156x Lernbox b</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Polypropylen, stapelbar,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">BxHxT 312x75x427 mm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Deckenhohe Verblendung der Schrankwand (ca. 400 mm)</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Schrankwand mit Lernschränken</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAICHOBAAA" RNoPart="20">
          <Qty>1.000</Qty>
          <QU>Stk</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schrankwand, bestehend aus den folgenden Bestandteilen:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">3x Hochschrank für max. 5 Ordnerhöhen</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2 Flügeltüren vollverglast,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fachböden im Raster verstellbar,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sockelhöhe 110 mm anthrazit</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Höhe 2090 mm, Breite 600 mm, Tiefe 550 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Innenausstattung Fachboden fest 4x</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einschl. Griffen</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">verschließbar</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">3x Aufsatzschrank</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2 Flügeltüren voll,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Einhängeschiene für Leiter</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fachböden im Raster verstellbar,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sockelhöhe 110 mm anthrazit</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Höhe 760 mm, Breite 1200 mm, Tiefe 550 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Innenausstattung Fachboden fest 1x</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einschl. Griffen</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">verschließbar</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leiterschiene:</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Als Metallschiene zwischen Schrank und Aufsatzschrank</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">fest verankert, Dicke min. 2 mm; mit Aussparungen zum</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einhängen einer Anlegeleiter; Schranktüren bei</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">eingehängter Leiter zu öffnen.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Deckenhohe Verblendung der Schrankwand (ca. 400 mm)</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Anlegeleiter</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit 2 Paar Einhängehaken, Aluminium, Belastbarkeit 150</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">kg, B/H = 450/2330 mm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Parkschiene für Anlageleiter</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Schrankwand</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAICHOCAAA" RNoPart="30">
          <Qty>1.000</Qty>
          <QU>Stk</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sicherheitsausstattung, bestehend aus den folgenden Bestandteilen:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Erste-Hilfe-Schrank mit Füllung nach DIN</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">13157,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1 verschließbare Tür, 2 verstellbare Böden, geräumige</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Türfächer, Kunststoff weiß, B/H/T = 315/430/150 mm</span>
               <br/>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Behälter mit Füllung, 1 Löschdecke nach DIN 1869, 1</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Paar Hitzeschutz-Handschuhe KSA, Drehverschluß,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stahlblech kunststoffbeschichtet RAL 3000 Feuerrot</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">B/H/T: 315/320/125mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Aufschrift Löschdecke</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Sicherheitsausstattung</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
        </Itemlist>
       </BoQBody>
      </BoQCtgy>
      <BoQCtgy ID="AAAAAAAAICHOEAAA" RNoPart="5">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>Zubehör</span>
        </p>
       </LblTx>
       <BoQBody>
        <Itemlist>
         <Item ID="AAAAAAAAICHOFAAA" RNoPart="10">
          <Qty>1.000</Qty>
          <QU>Stk</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zubehör, bestehend aus den folgenden Bestandteilen:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">12x Teclubrenner Propangas mit Haltefuß</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gasbrenner mit Luftregulierung, Nadelventil zur</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gasregulierung, Sparflamme innen, entspricht DIN</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">30665, max. Flammentemperatur 1500 °C</span>
               <br/>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Sicherheits-Gasschlauch Rot 1000mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schlauch für Bunsen- und Teclubrenner, innere</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Edelstahlstützspirale, beiderseits verstärkte</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Endmuffen für sichere Handhabung, Farbe Rot</span>
               <br/>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">11x Sicherheits-Gasschlauch Rot 1500mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schlauch für Bunsen- und Teclubrenner, innere</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Edelstahlstützspirale, beiderseits verstärkte</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Endmuffen für sichere Handhabung, Farbe Rot</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Zubehör</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
        </Itemlist>
       </BoQBody>
      </BoQCtgy>
      <BoQCtgy ID="AAAAAAAAICHOGAAA" RNoPart="6">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>Sonstiges</span>
        </p>
       </LblTx>
       <BoQBody>
        <Itemlist>
         <Item ID="AAAAAAAAICHOHAAA" RNoPart="10">
          <LumpSumItem>Yes</LumpSumItem>
          <Qty>1.000</Qty>
          <QU>psch</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inbetriebnahme Gas-Laborsicherungen vor Abnahme</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Gas-Laborsicherungen</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAICHOIAAA" RNoPart="20">
          <Qty>3.000</Qty>
          <QU>Stk</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Teilnahme an Bau/ Planungsbesprechungen am Ort der Leistungserstellung inkl. Anfahrt</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Teilnahme an Baubesprechungen</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAICHOJAAA" RNoPart="30">
          <Qty>1.000</Qty>
          <QU>Stk</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ortstermin zur Inbetriebnahme</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einschließlich vollständiger Demonstration und Schulung der Lehrkräfte vor Ort inkl. Anfahrt</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Inbetriebnahme</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAICHOKAAA" RNoPart="40">
          <Qty>10.000</Qty>
          <QU>Stk</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schlüssel für Schlüsseltaster</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Schlüssel für Schlüsseltaster</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAICHPFAAA" RNoPart="50">
          <Qty>10.000</Qty>
          <QU>Std</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stunden eines Facharbeiters zum Nachweis,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">auf besondere Anordnung der Bauleitung</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für unvorhergesehene Arbeiten.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Facharbeiterstunden</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
        </Itemlist>
       </BoQBody>
      </BoQCtgy>
     </BoQBody>
    </BoQCtgy>
   </BoQBody>
  </BoQ>
 </Award>
</GAEB>
